Vertical Rack Bonding Busbar Kit (RBB)
72" Vertical Rack Bonding Busbar (RBB) Kit (Part# GBP-RGB-V72-01-Kit)
For brief step-by-step instructions on how to place an order on our website, click here.
The Importance of Electronic Equipment Grounding
Electronic equipment can be sensitive to stray currents, electromagnetic interference, electrostatic discharge and other electrical disturbances “noise”. To prevent electrical disturbances from affecting computers and other electrical equipment two entirely different and separate grounding systems are required. The power distribution system must be grounded and the computer equipment and enclosures should be connected to a grounding grid or common bonding network.
The goals of the grounding system within a data center are to equalize electrical potentials and to create a low impedance path to ground. You want a grounding system that directs damaging currants away from the equipment. TIA-607-C requires each rack to bond directly to the grounding grid or common bonding network, directing current away from sensitive electronics.
7.1.4 Cabinets and racks
Rack bonding busbars (RBBs) are recommended for cabinets and racks that need to support multiple unit (equipment) bonding conductors. Cabinets, racks, and other enclosures in computer rooms shall not be bonded serially; each shall have their own dedicated bonding conductor to the bonding network, telecommunications grounding busbar, or telecommunications main grounding busbar.
- Equipment rack bonding busbars serve as a common and accessible grounding point for all electronics mounting in an equipment rack or cabinet.
- The rack bonding busbar provides a convenient ground path between equipment mounted in a rack and the telecommunications bonding backbone.
- Each vertical rack bonding busbar runs the length of the rack and is pre-drilled to accommodate up to 36 flex unit bonding conductors for rack mounted equipment.
- Each piece of equipment is bonded directly to the busbar with a short flex unit bonding connector.
- 1 – 72” tinned copper vertical rack bonding busbar
- 3 – 11/16” white Delrin insulators (to insulate the busbar from the rack and creating intermediate grounds)
- 6 – #12 x 5/8 zinc plated screws